Low temperature DEC process with KVS dries the fresh air in the first rotor (Dezecor) and cools the warmed up and dry air with adiabatic exhaust air moistening at the second, sensitive KVS. The exhaust air is warmed by regeneration temperature..This hot air drives the rotor, it takes the stored dampness from the Dezecor with further air under cooling.
For the fresh air side there is enthalpie reduction, for the exhaust air enthalpie recovering is used. The heat is the driver of the Desi process. Besides, the fresh air can be dried with regeneration temperature. With 55°C regeneration makes the fresh air 4 gs / kg humidified. For the adiabatic exhaust air moistening HD Humidifier with summer / winter change-over or contact humidifier is used. Ventilating fans with frequency umformer and volume control. Complete process regulation of the rotors, bypass damper, regeneration and humidifier. Control Panel includes electric switch board, interface and modem.
Fresh air for banks, blocks of flats, office houses, cinemas, schools and study places, lab constructions, packing place, food, chill piece of furniture, clean rooms. Process rooms, micro-production rooms and buildings with active moist control. Combination with cooling component.
Do not hesitate to contact us - we are available for any questions and further information for you at any time.